Plumbing Repairs Espanola, New Mexico
Reliable Tech Heating Cooling and Plumbing prides itself on being the most reliable and knowledgeable plumber in Espanola, NM. No job is too large or too small.
For all those little jobs from fixing faucets, stopping drips, replacing old piping, replacing valves, repairing toilets, repairing water heaters, fixing underground water leaks, fixing gas lines, call Reliable Tech Heating Cooling and Plumbing.
Replace fixtures to a single knob on 2 showers and a knob, leaky showers.
North Prince Dr ESPANOLA, NM
Technician arrived on site to find a leak at the external water inlet, that the toilet had a cracked valve and broken seat, that the kitchen faucet was cracked and leaking and that the drain from the kitchen sink was clogged. Because it is a mobile home, specialty parts were ordered and picked up in Santa Fe, and so the toilet was replaced, the kitchen sink was replaced, and the water inlet was replaced and wrapped in insulation (see attached photos) The kitchen drain was taken apart, the P-trap and pipes were leaking and clogged with garbage and cigarette butts, and more cigarette butts were clogging the drain line passed the ptrap and leading out of the mobile home, and so the whole system was snaked. P-trap and PVC piping was replaced, and everything is working properly with no leaks.
North Monterey Lane ESPANOLA, NM
Bring a tall ladder 8ft + Bring a universal capacitor. Be sure to test blower motor/capacitor. Barry wants another year out of unit,
N. Riverside Dr. ESPANOLA, NM
Technician replaced water pump on aerocool evaporative cooler. all components were tested and unit is working properly
Los Arboles Circle ESPANOLA, NM
installed 40 gal gas water heater
US 84/285 ESPANOLA, NM
Replaced 007 Boiler pump.
Abbey lane ESPANOLA, NM
Technician Installed a Rheem 40 gallon Electric water, Expansion Tank and Flex connectors. All components were tested.
Middle San Pedro ESPANOLA, NM
Installed a Trane 80,000 BTU
Sunset ESPANOLA, NM
Tech inspected drain line . No leaks or openings
Caminio Rio Seca ESPANOLA, NM
Tech tightened fittings on 2 separate leaks on vacuum pumps. Fittings are no longer leaking but if they persist new hose must be installed for those sections.
N Riverside Dr. ESPANOLA, NM
Unit freezing up, restriction TXV non-op, replace evap coil, recover 410-A pump down system, recharge with 410-A and check operation.
Ziegler St. Espanola NM ESPANOLA, NM
I located the leak on the split system, the connection to the A coil was where it was at I replaced it and recharged with 2 more LBS of R22 Freon.
N Riverside Espanola, NM ESPANOLA, NM
Technician did diagnostic check on york unit and found low pressure on refrigeration lines. Unit must be charged with R-22 to bring pressure back up to proper levels.
Simmons Lane Espanola NM ESPANOLA, NM
Lower San Pedro Rd ESPANOLA, NM
Calle Lucero ESPANOLA, NM