Plumbing Repairs Espanola, New Mexico
Reliable Tech Heating Cooling and Plumbing prides itself on being the most reliable and knowledgeable plumber in Espanola, NM. No job is too large or too small.
For all those little jobs from fixing faucets, stopping drips, replacing old piping, replacing valves, repairing toilets, repairing water heaters, fixing underground water leaks, fixing gas lines, call Reliable Tech Heating Cooling and Plumbing.
Technician replaced water pump on aerocool evaporative cooler. all components were tested and unit is working properly
Los Arboles Circle ESPANOLA, NM
Replaced 007 Boiler pump.
Abbey lane ESPANOLA, NM
Technician Installed a Rheem 40 gallon Electric water, Expansion Tank and Flex connectors. All components were tested.
Middle San Pedro ESPANOLA, NM
Installed a Trane 80,000 BTU
Sunset ESPANOLA, NM
Tech inspected drain line . No leaks or openings
Caminio Rio Seca ESPANOLA, NM
Tech tightened fittings on 2 separate leaks on vacuum pumps. Fittings are no longer leaking but if they persist new hose must be installed for those sections.
N Riverside Dr. ESPANOLA, NM
Unit freezing up, restriction TXV non-op, replace evap coil, recover 410-A pump down system, recharge with 410-A and check operation.
Ziegler St. Espanola NM ESPANOLA, NM
I located the leak on the split system, the connection to the A coil was where it was at I replaced it and recharged with 2 more LBS of R22 Freon.
N Riverside Espanola, NM ESPANOLA, NM
Technician did diagnostic check on york unit and found low pressure on refrigeration lines. Unit must be charged with R-22 to bring pressure back up to proper levels.
Simmons Lane Espanola NM ESPANOLA, NM
Lower San Pedro Rd ESPANOLA, NM
Calle Lucero ESPANOLA, NM