Furnace Service and Repair Los Alamos, New Mexico
If your heating system in Los Alamos, NM is not working it is likely your furnace needs repair or service. At times the fix is simple, other times it is not. Our heating and furnace service technicians have years of experience working on furnaces like yours in Los Alamos, NM. Reliable Tech Heating Cooling and Plumbing has service vehicles on call that are fully equipped with the tools and parts necessary to get your furnace back up and operating.
Our furnace repair, furnace service or replacement pricing is very competitive. Our estimates are always firm with no hidden surprises. You can rely on Reliable Tech Heating Cooling and Plumbing to advise you properly and to do excellent work promptly. Ask us about maintenance agreements for your high efficiency furnace today.
Diagnostic visit- Furnace makes a clicking noise and does not stay on. The furnace will click on and off consistently. Check flame sensor? Thermostat? Diagnose issue and fix that day if possible. We installed the furnace 2 years ago, furnace is under warranty however the service membership is not. Explain service member savings, I didn't have enough information for her.
Paige Loop East LOS ALAMOS, NM
The furnace is working well just has an extremely loud noise coming from it. It is a Trane brand furnace unknown model.Check fan wires too lower blower speed, already set at lowest setting.. customer purchased p/m contract, check electrical, blew out burner area and cleaned flame rod..check for gas leaks and co..change filters customer supplied...1st visit on new contract.
Azure Dr. White Rock, NM LOS ALAMOS, NM
Run furnace diagnostic, change filters, check C/O levels. discuss gas and plumbing water lines with Laurie, she is wanting to book us for some re-routing in her gas lines, etc.
46th Street LOS ALAMOS, NM
Install a new Trane XV80 21” 5 ton up flow 100,000 BTU variable speed two stage gas furnace with new gas stop valve, gas flex line, new programmable thermostat, run new thermostat wire, reconnect to existing flue pipe, install 2- 6” combustion air piping to provide proper combustion air to water heater and furnace, or 1- 8” pipe, start and test operation, clean up job site, and dispose of old equipment.
Sioux Street LOS ALAMOS, NM
Upon arrival found extremely dirty filter p.m. system clean flame Rod checked electrical relocate capacitor check times two capacitors all checks good.. blew out burners and system,.replaced X2 filters 12x20x1... unit running at time of service.
Broadview Drive LOS ALAMOS, NM
ECM Retrofit Motor. Service Member Program paid in full.
Rover Blvd LOS ALAMOS, NM
Tech performed diagnostic/gas leak detection on 3 year old trane unit we installed. Trane XL80 no gas present.
Camino Manzana, Los Alamos, NM LOS ALAMOS, NM
tech performed diagnostic check allied aireas furnace and found faulty pressure switch. Switch is registering intermittent signal and causing unit to short cycle. Switch registers a fault code of open with inducer motor on and closed with inducer motor off.
45th Street D LOS ALAMOS, NM
Needs two pressure switches. Boiler needs expansion tank zone valve and double check valve on boiler.
Bryce Ave LOS ALAMOS, NM
Annual Maintenance. Started up furnace. Did a CO test, changed filet, gas test all is operating properly
Canada Way, White Rock, NM LOS ALAMOS, NM
Replace fuse and inspect furnace.
El Conejo LOS ALAMOS, NM
Inspected furnace CO test, gas test operation of furnace is operating properly
White Street Unit C LOS ALAMOS, NM
St LOS ALAMOS, NM
Collen Ct LOS ALAMOS, NM