Furnace Service and Repair Santa Fe, New Mexico
If your heating system in Santa Fe, NM is not working it is likely your furnace needs repair or service. At times the fix is simple, other times it is not. Our heating and furnace service technicians have years of experience working on furnaces like yours in Santa Fe, NM. Reliable Tech Heating Cooling and Plumbing has service vehicles on call that are fully equipped with the tools and parts necessary to get your furnace back up and operating.
Our furnace repair, furnace service or replacement pricing is very competitive. Our estimates are always firm with no hidden surprises. You can rely on Reliable Tech Heating Cooling and Plumbing to advise you properly and to do excellent work promptly. Ask us about maintenance agreements for your high efficiency furnace today.
Goodman model Furnace, Tech did inspection on heating systems
Tano Ridge Rd, Santa Fe, NM SANTA FE, NM
Tech performed diagnostic on furnace to find gas leak search and CO negative. Furnace is working properly. Tech recommends cleaning the furnace and blower motor.
Calle de Rincon Bonito, Santa Fe, NM SANTA FE, NM
Tech found faulty tstat sensor on Lochinvar combi unit. Tech reset the unit and tstat and it fired up. Tech recommends heat exchanger cleaning and fernox treatment.
Canyon Rd. Apt 10 SANTA FE, NM
Furnace inspection on Hiel 80% checked capacitor, wiring, blower motor, changed fitler. 0ppm CO no gas leak.
San Felipe Circle, Santa Fe, NM SANTA FE, NM
Tech completed furnace start up on Rheem 80% system. Tech checked wires + volts amps. Filter was cleaned and sparks igniter was checked. Nuvo filter was replaced. 0ppm capacitor is within mfd
Alto St, Santa Fe, NM SANTA FE, NM
Furnace wasn't firing up, got heater working.
Cerrios Rd, Santa Fe, NM SANTA FE, NM
Tech completed maintenance on Heil 80% furnace. Teach checked wires, volts, amps, and capacitor. Co test 0ppm and cleaned filter.
Calle Colina SANTA FE, NM
check up on furnace
Camino De Chelly SANTA FE, NM
Maintenance on furnace.
Camino De Chelly, Santa Fe, NM SANTA FE, NM
Tech completed furnace inspection and start up. Tech checked wires, amps, and volts, also cleaned Trane clean effects. TRANE XL80 10,000 BTU model TD
Calle Colina, Santa Fe, NM SANTA FE, NM
Replace gas valve and pilot assembly. Left furnace off due to gas leak
Boneyard Rd. Espanola, NM SANTA FE, NM
Diagnostic on Furnace. Found gas leak on furnace, need to test gas line, and replace all shut offs on heating units. per state code.
Camino De La Luz, Santa Fe, NM SANTA FE, NM
Flame Sensor Cleaned
Alteza SANTA FE, NM
Furnace maintenance/ check up. Unit Red tagged.
Calle Agua Clara, Santa Fe, NM SANTA FE, NM
Flame sensor cleaned. Lennox AC & Furnace
Salvadro Pl, Santa Fe, NM SANTA FE, NM
Found multiple cracks and holes in heat exchange due to rust buildup. Inducer motor has also failed which caused unit not to work. Unit is red tagged.
La Viveza Ct, Santa Fe, NM SANTA FE, NM
Install Trane furnace
Camino Piedra Lumbre SANTA FE, NM
Dr SANTA FE, NM
Loma Linda SANTA FE, NM
Milagro Oro SANTA FE, NM